KJT Dosing Pot
Dosing Pots are designed to provide the means of introducing chemical solutions such as corrosion inhibitors into closed heating and chilled water systems. The specific size of the dosing pot in a system is not critical as the pot can be filled multiple times to obtain the correct concentration. The benefit of using a smaller unit, is that it is easier to physically handle and also allows for more accurate dosing. However, since chilled water systems generally require higher concentrations of dosing chemical, usually glycol, to be dosed into the system a larger dosing pot may be required. For concentration levels always consult the manufacturer.
SPECIFICATIONS / USAGE AREAS
• Dosing pots provide safe and controlled chemical introduction into sealed heating and cooling water systems.
• Dose chemicals without interrupting system operation.
• Supplied fully assembled for ease of installation and facilitate simple, regular on-going maintenance of your heating or chilled water system.
To prevent scalding safe practice must be observed when venting or draining hot water at pressure.
Maximum Operating Temperature
Maximum Operating Pressure
1000 kPa (10 bar)
Conform to the requirements of Pressure Equipment Directive 2014/68/EU and are designed and manufactured according to Sound Engineering Practice (S.E.P).
|Height Between Flow/Return Valves||h2||mm||295||420||425||550||695||600|
|Air Vent Valve Assebly Connections||N1||inch||½”||½”||½”||½”||½”||½”|
|Filling Valve Connection||N2||inch||1″||1″||1″||1″||1″||1″|
|Return Valve Connection||N3||inch||1″||1″||1″||1″||1″||1″|
|Flow Valve Connection||N4||inch||1″||1″||1″||1″||1″||1″|
|Drain Valve Connection||N5||inch||1″||1″||1″||1″||1″||1″|
|Bracket Width Dimension||a||mm||185||215||265||265||265||320|
|Bracket Height Dimension||b||mm||90||205||210||335||480||405|
KODSAN reserves the right to change the product specifications, technical information and installation diagrams without any notifications.
All information written on this page can not be copied or used without permission of KODSAN. Kodsan can not be held responsible if any of the technical information and
schemes are considered exemplary by third parties.